An alternate system runs on the fog or good mist injected into the intake air stream. Although many commercial systems are available, growers can assemble and install their own system using a high pressure piston pump and fog nozzles. The essential components are demonstrated in Fig. 1. A two-stage system controlled by a two- stage thermostat enables more water to be employed on excessively warm, bright days. Temperature settings ought to be 5-10°F apart.
Algae growth in the pads can become a problem which will reduce the effectiveness of the machine and lead to accelerated deterioration of the pads. The addition of an algaecide to the water supply will help in control.
It really is desirable, especially in hard water areas, to include a wetting agent to the water to obtain additional uniform wetting of the pads. A commercial material or liquid home detergent at the price of 2 tablespoons per 100 gallons may be used.
Water for the pads ought to be clean and lower in mineral content to avoid clogging and coating of the pads. A pump, pipes and gutters are used to recirculate the drinking water. A flow rate 113 gallon per minute per linear foot of pad system should be provided to guarantee adequate wetting.
In the most typical cooling system (fan and pad), the fans draw air through wet pads that lengthen the length of 1 endwall or sidewall. Aspen and coated cellulose are normal pad materials that always have life of 1 to 3 years. Approximately one sq . foot of pad are is needed for 20 square ft of floor area.
Love Greenhouse Auto Vent and also would love to figure out more?